|A peerless boiler to the left and a gas
water heater to the right.
I see 3 problems
with this picture. first and potentially most
dangerous is the flexible gas tubing going to
the water heater on the left, this flexible gas
line has been recalled because it develops small
pin holes and gas leaks out, very dangerous, the
relief valve in the background is not extended
far enough down towards the ground and can cause
someone to be burned if it goes off.
coming out around the gauge is a possible carbon
monoxide leak. Have your equipment serviced by a
real plumbing and heating contractor every year.