Replacing an Aquastat
relay to a simple Aquastat.
First the reason I am
replacing the Aquastat relay with just a simple
aquastat and not using a relay on this boiler
(this may not apply to your needs) This Boiler
has a garage unit heater that is set up to have
hot water run through it all the time, so the
pump is running all the time and the boiler is
hot all the time. So there is no need for a
relay to turn the pump on. If it needed a relay
I would replace it with simple aquastat and a
fan center relay. Note If you did not understand
the previous paragraph, you should stop and call
a heating professional.
The next time I have to
do that I will add that scenario to this page.
If you need instructions for that now go to this
Does This Look
Like your boiler? All the controls are
behind the front cover. So remove the cover Turn
the switch to the boiler off. Warning the switch
may not turn all the power off. turn off breaker
too and test line to make sure power is off.
|About me |
Privacy policies |
Site Map |
Contact me |
Feed Back |
Annoyance Fee? |