When putting the burners back make sure the
center of the back of the burner goes over the
orifice nipple. and the front little pimple goes
into the little dimple on the tray.
If it is in correctly it will not move side
ways. then put the screw back. now the tray and
burners should feel like one piece the burners
should no have any play in them at all. Make
sure the pilot tube and the thermocouple are
facing towards you. Now slide the tray back in.
Line the union up and make sure both tabs drop
back in there slots on the left and right side
of the tray. Now normally I would just say
tighten up the union but we have to replace the
gas valve first.
|About me |
Privacy policies |
Site Map |
Contact me |
Feed Back |
Annoyance Fee? |